When heating and air conditioning problems strike, homeowners in Parrish, FL appreciate having access to high-quality HVAC services. That’s where we come in. When working with the experts at Air Now, you can rely on getting top-tier installations and repairs along with trusted customer care.
We also provide same-day service and are on call 24 hours a day, seven days a week and 365 days a year. There’s no need to fear when trouble occurs. We’re ready to help you out, whether it’s in the middle of the night, during the weekend or on New Year’s Eve.
Learn how you can save money on your next HVAC service call by looking at our coupons page today.
Common AC Problems to Watch Out For
Between the summer heat and humidity, you need your air conditioning unit to be working at all times, especially in the sticky summer months. So when it goes out in the middle of a heatwave and the temperature in your home is increasing into the uncomfortable zone, it’s time to call a reliable 24-hour emergency air conditioning repair company. Some common problems you might encounter with your system can include:
- Lack of cold air: Perhaps the most obvious issue with your system can be a lack of cold air, even when the thermostat is turned to a low setting. A complete lack of cooling, or even intermittent cooling, is a huge sign that there is something wrong with your unit. If cool air -- or enough cool air -- isn’t entering your home you should call for professional services.
- Air isn’t flowing through vents
: If you notice the air isn’t flowing through your vents properly, it can cause a series of issues. It can cause your system to work harder than it needs to in an attempt to cool your home. This can leave your home insufficiently cooled, and it can cause a rise in your monthly utility bills.
- Malfunctioning thermostat
: If your home isn’t reaching the desired temperature, or if parts of your home are warmer than others, it can be a sign of a malfunctioning thermostat.
- Moisture leaking from the unit
: If you notice moisture leaking from your system, or around it, it can indicate a blocked or broken drain tube. You should call a professional to inspect the issue as it can also be a refrigerant leak. Coming into contact with refrigerant can lead to health problems if not handled correctly.
If you’re currently without AC, don’t wait till the next day to get the repairs you need. Air Now has you covered with 24-hour emergency AC repairs so you and your loved ones can stay safe and comfortable at home.
AC Repairs and Installations
All homeowners should have an idea about the importance of an air conditioning system that runs smoothly and efficiently. If your HVAC isn’t operating like it’s meant to do, it may have to work harder than it should. This can have a bad influence on the cost of your energy bill impact the temperature in your home. The pros at Air Now will be able to deliver reliable AC repair and maintenance service to you.
A time will come when repairs simply won’t be worth the cost anymore and a new system must be put in. We can also conduct air conditioning installation service at your convenience. We take it upon ourselves to ensure your home is kept cool throughout the year. It’s our privilege to lend a hand when it comes helping you manage utility and maintenance costs.
Air Duct Cleaning and Repairs
The most essential piece of equipment in an HVAC system is the air ducts. It’s of the utmost importance, therefore, they’re kept in the best condition possible so they continue delivering a seamless flow of cool air throughout your home. Cracks and holes in ducts can let air escape and contaminants to enter the system. We want to help you keep energy costs low while each room in your home stays cool with our air duct installation and air duct repair services.
Air duct cleaning is also a crucial part of ductwork maintenance. By cleaning your ducts you’re getting rid of dust and spores that could otherwise make their way into your home. This can put people inside at risk of asthma attacks, respiratory infections, allergy attacks or sinus infections. Hire a duct cleaning service and protect the health of everybody under your roof.
Discover our latest reviews and testimonials to learn what people in your area have to say about us.
for Parrish, FL
Eirec - Parrish, FL
Janet - Parrish, FL
Thorough examination of problem!
Janet - Parrish, FL
Janet - Parrish, FL
DON - Parrish, FL
Service call, new customer. 2014 equipment installed early 2015. Original equipment to the manufacturing of dwelling only comes with a five year parts warranty. System does not have warranty Upon arrival found system extremely low on refrigerant. 50/200 psi Fairly large refrigerant leak inside the refrigerant circuit. Electronic leak test needs to be performed in order to allocate the bad part. *Evaporator coil is heavily rusted and dirty on the backside *Condensing unit coil showing spots of corrosion. *. Blower motor capacitor reading 4.4 ÂµF out of the 7.5 extremely low needs to be replaced * outdoor compressor capacitor also below specs. 40/5 ÂµF control * Contactor at the condensing unit, on off switch burnt and pitted. Not providing a solid clean connection. * low-voltage wiring outside the condensing unit looks like it received damage from lawn maintenance possibly wrapped around a Weedwhacker. Red exposed, all 8 wires need to be repaired. Condensing it holds 5 lbs. 10 oz. Le
YORK 18 SEER EFFICIENCY (AT MAX COOLING) MODULATING INVERTER TECHNOLOGY HEATPUMP **EXCEEDS 2023 EFFICIENCY MANDATES** 10 YEARS PARTS WARRANTY *10 YEARS LABOR WARRANTY* 10 YEARS COMPRESSOR WARRANTY 1 YEAR ESA FAMILY PLAN ALL TAXES, PERMIT FEES AND INSTALLATION INCLUDED PREMIUM INSTALLATION INCLUDES; *FREEZE PROTECTION (PROTECTION FOR THE EVAP COIL AND COMPRESSOR DAMAGE *4â€ WHOLE HOUSE FILTRATION SYSTEM *ULTRAVIOLET LIGHT SYSTEM (PROTECTION AGAINST MOLD AND MILDEW WITHIN THE AIR HANDLER) *DUAL WATER SAFETY PROTECTION SWITCHES *SECONDARY CONDENSATE PAN *DRAIN PAN TREATMENT *NEW ANTIMICROBIAL LINED SUPPLY AND RETURN PLENUMS* *SANITIZE DUCT SYSTEM (MAIN SYSTEM) *VENT DRAIN LINE *INSTALL DRAIN GUARD SYSTEM *DITEK KOOL GUARD 2 UNDER AND OVER VOLTAGE PROTECTION SYSTEM* *HONEYWELL T6 PRO THERMOSTAT **SPECIAL INVERTER PRICING-GOOD FOR 2 WEEKS FROM 05/06/2022** *WHOLE HOUSE AIR PURIFICATION SYSTEM $897.00 WITH INSTALLATION OF NEW SYSTEM (REGULAR PRICE $1374.00) ***0% FINANCING AV
May 25, 2020 updated quote As we discussed on original visit this is the confirmed correct quote for your repair. York will not cover refrigerant. This is due to you not having a 10 year parts 10 year labor warranty. You currently have a 10 year parts one year labor warranty. At minimum this is the options for you to get the system back up and running. I did verify everything through the manufacture as I was telling you that night. York only covers refrigerator if the customer has a 10 years parts and a 10 years labor through the manufacture and only if itâ€™s a coil or compressor replacement. Eric I did what I could to help out through the manufacture, but I was able to get you the refrigerant just about at cost I hope this helps. Upon arrival found compressor not working, plug was not on compressor both depends on the compressor and the plug rotted away. Loud sparking and arcing noises. Overall parts that need to be replaced. Compressor, compressor wire harness, contactor, capacito
arrived to find the downstairs system was operational but not cooling. Temperature split across the coil 78/73.7. Found ice formed on the bottom sides of the evaporator coil and the coil is rusted. Disconnected the orange wire to run the condenser in heat and thawed the coil. Returned the system to cooling and checked the operational pressures, 100/298. Sprayed the evaporator coil with liquid detector, found leaks at the bottom right side of the coil and at the TXV capillary tube assembly. Performed the system check on the upstairs unit. Cleaned and flushed the drain line. Checked the amp draw on the: blower 1.38 max 1.9; blower capacitor 4.12 on a 7.5; heat strip 21.28; condenser fan .89 max 1.1; compressor 7.35 max 12.8; SLT 57; LLT 89; start capacitor 40.16/5.11 on a 40/5 +/- 5%. Checked the electrical connections, float switch and coils.
Service call system not cooling New customer. Eric if you need anything adjusted or any information for the insurance company call or text me tomorrow. Iâ€™ll be up and alive working most likely from 8 AM till 11 PM to call anytime. Sooner we call York the better. I will call them in the morning to see the availability of this compressor so that when you contact me Iâ€™ll have an answer how long itâ€™ll take to ship to us. Eric right off the bat, I highly recommend hey semi annual maintenance program. Most of which like with our company we can find issues before they happen so you rarely or never had downtime. Right off the bat Eric is getting approval from his home insurance who told him they will reimburse him for what he manufactures warranty does not cover. He is calling insurance company tomorrow getting pre-authorization and he will either contact the office or me directly to move forward at that point he will I have an answer on what weâ€™re doing what parts were getting and