When homeowners in Bradenton, FL are plagued with heating and air conditioning issues, they can appreciate having access to first-rate HVAC services. That’s where we come in. When working with the team of professionals at Air Now, you can bet on receiving dependable installations and repairs accompanied by superior customer care.
We’re able to perform same-day service and are also available by phone 24 hours a day, seven days a week and 365 days a year. There’s no need to fear when an emergency strikes. We’re here to help you out, whether it’s in the middle of the night, during the weekend or on a holiday.
Discover how to save money your next HVAC service call by checking out our coupons page today.
What to Expect During an AC Tune-Up
When you call a professional to inspect your air conditioner, you can expect him or her to perform a complete evaluation of your unit during both a 24-hour emergency service call or a routine maintenance request. Some tasks you can expect a technician to complete are:
- Check the refrigerant: A professional will check your system’s refrigerant to make sure it has the correct amount. He or she will also check for any leaks, especially if the level is lower than it should be.
- Inspect the air ducts: Experts will check the air ducts for debris and potential leaks. If any issues are noticed, technicians will recommend a solution to repair the problem.
- Check the evaporator coil: Professionals will inspect the evaporator coil to make sure the right amount of air is flowing through it, and to determine if there are any other issues with the unit.
- Check the electric control sequence: Experts will verify the correct electric control sequence and make sure that the cooling and heating sequences are not operating at the same time.
- Inspect the electric terminals: Professionals will inspect the electric terminals to make sure everything is working as expected. If needed, technicians may apply nonconductive coating.
- Check all components: Technicians will check all of the system’s components to make sure they are working properly. This can include applying oil to the motors and examining the belts.
- Check the thermostat: Experts will examine the thermostat to make sure it is properly controlling your indoor climate.
To prevent emergency repairs with your air conditioning system, it’s recommended that you schedule routine maintenance at least once a year before the summer heat hits. If you’re without AC right now, don’t wait. Air Now is available for 24-hour emergency AC service so you never have to suffer through a night in the Florida heat.
AC Repairs and Installations
Maintaining an air conditioning system that runs effectively and efficiently should be a priority to all homeowners. If air isn’t circulating through your HVAC system like it’s designed to do, it has to work harder and will, therefore, increase the cost of your energy bill. It can also have an influence on the temperature in each room of your home. Our crew members at Air Now can conduct top-notch AC repair and maintenance service.
Sooner or later, though, repairs simply won’t cut it anymore and a brand new system must be installed. If this is the case, we can also perform an air conditioning installation service at your convenience. We take pride in taking it upon ourselves to make sure your home is kept cool all year long. We consider it our duty to lend a hand in terms of helping you manage your utility and maintenance costs.
Air Duct Cleaning and Repairs
When it comes to a home’s HVAC system, the most important piece is the air ducts. And for this reason, they must be kept in pristine condition to continue circulating cool air throughout a building seamlessly. Cracks and holes in ducts can lead to air escaping and contaminants making their way into the system. Let us help you keep energy costs down and the air in your home clean with our air duct installation and air duct repair services.
Air duct cleaning is an integral part of ductwork maintenance. If you ignore it, dust particles and spores could enter the vents in your home. This can put everybody inside at risk of respiratory infections, allergy attacks, asthma attacks or sinus infections. Protect the health of every person under your roof by hiring a duct cleaning service.
Check out the latest reviews and testimonials from our customers to find out what people are saying about us.
for Bradenton, FL
Richard - Bradenton, FL
Our AirNow technician that handle our service visit today was amazing. He was very professional and courteous. He was very knowledgeable installing our Ecobee thermostat. He patiently explained everything he was doing and answered all my questions. A big shoutout to the AirNow technician Brian! Thank you.
Great service and excellent installation
Robert - Bradenton, FL
Everything was done as planned and all the equipment was as described.
Margrit - Bradenton, FL
Awesome AC service
CAROL - Bradenton, FL
Air Now has never failed to provide excellent service!
MARY - Bradenton, FL
Your technician remembered servicing us in the past and remembered where the furnace and air conditioner were located. He let us know what portions of the service he was completing and informed us what he did.
Arrived to find the thermostat for the York unit was blank. Checked the air handler and found the system was off due to the drain line being backed up and the float switch was full. Blew out the drain line, poured cleaner into it and tested the system. Temperature split 78.4/59.1; blower 3.77 max 6; condenser fan 1.15 max 1.3; compressor 15.18 max 24.3; SLT 62; LLT 81. Flushed the drain line. Found the older Goodman system was not cooling due to the thermostat being set for heat not cooling. Checked the temperature split on the Goodman 77.7/54.6. Found the drain line was blocked. Cleared, cleaned and flushed the drain line.
With Matt, tested the system operations, made adjustments to the blower speed, removed the 4â€ filter and installed an 18x18x1 at the grill, fixed a loose connection in the drain line.
Installed tested and programmed customer supplied thermostat. Working great at also checked temp split to ensure everything working fine 20 degree split after running for 5 mins
ESAPTU clean and flush drain line change filter check system for UV system does not have one. Bacterial growth present inside air handler. Checked all electrical components inside air handler all within spec. 21Â° split and cooling 25Â° split and heating. Checked all electrical components inside condenser all within spec. Capacitor at 100%
ESA one of two cleaned and flushed drain line change filter checked UV checked all electrical components inside air handler 21Â° split in cooling 27Â° split and heating heat strips read 33 A. Checked all electrical components inside condenser all within spec capacitor at 100% suction line temp 52Â°.